ISO 16813:2006 is one of the ISO building environment standards. It establishes the general principles of building environment design. It takes into account the need to provide a healthy indoor environment for the occupants as well as the need to protect the environment for future generations and promote collaboration among the various parties involved in building environmental design for sustainability. ISO16813 is applicable to new construction and the retrofit of existing buildings.
Energy efficiency can be improved even more in central heating systems by introducing zoned heating. This allows a more granular application of heat, similar to non-central heating systems. Zones are controlled by multiple thermostats. In water heating systems the thermostats control zone valves, and in forced air systems they control zone dampers inside the vents which selectively block the flow of air. In this case, the control system is very critical to maintaining a proper temperature.
It’s a rare occasion for a problem to arise with your heating or cooling equipment at a convenient time. In fact, we’re not even certain such a time exists! That’s why the team at HVAC & Plumbing Unlimited stands ready to provide complete emergency heating and cooling repairs. No matter the time of day or the day itself, we can be on the way and ready to provide prompt, cost-efficient services to our Alexandria clients.*
Our furnace quit lighting yesterday. I called Cool Tech around 7pm and they offered to come out after hours, but I chose to set up an appointment today. The technician John called me at 7:30am and was there about 8am as promised. He was very courteous and replaced the igniter quickly. The heater is back to working properly. This is my second time hiring Cool Tech and they will continue to be my go-to heating and air conditioning guys.
This job involves removing the access panel, loosening a couple of bolts that hold the blower motor at the proper tension, and adjusting its distance or realigning the belt. In many cases, it’s a good idea to remove the belt and buy a replacement at a home center. Last, when reinstalling the belt, be careful not to over-tighten it; this can wear out the motor bearings.
If you already have a newer condenser, the worst noise is probably coming from the compressor. (Fans on newer units are very quiet.) Contact the manufacturer to find a sound blanket for your model or buy a universal blanket (search online for “compressor sound blanket”). Installation is easy. Don’t bother putting a blanket on an old unit—you’ll still hear the noisy fan. Here are other possible solutions for a noisy air conditioner.
Ground source, or geothermal, heat pumps are similar to ordinary heat pumps, but instead of transferring heat to or from outside air, they rely on the stable, even temperature of the earth to provide heating and air conditioning. Many regions experience seasonal temperature extremes, which would require large-capacity heating and cooling equipment to heat or cool buildings. For example, a conventional heat pump system used to heat a building in Montana's −70 °F (−57 °C) low temperature or cool a building in the highest temperature ever recorded in the US—134 °F (57 °C) in Death Valley, California, in 1913 would require a large amount of energy due to the extreme difference between inside and outside air temperatures. A few feet below the earth's surface, however, the ground remains at a relatively constant temperature. Utilizing this large source of relatively moderate temperature earth, a heating or cooling system's capacity can often be significantly reduced. Although ground temperatures vary according to latitude, at 6 feet (1.8 m) underground, temperatures generally only range from 45 to 75 °F (7 to 24 °C).
Window unit air conditioners are installed in an open window. The interior air is cooled as a fan blows it over the evaporator. On the exterior the heat drawn from the interior is dissipated into the environment as a second fan blows outside air over the condenser. A large house or building may have several such units, allowing each room to be cooled separately.
Before opening the electrical cover on the A/C unit, be sure to shut off all power to the compressor unit and the indoor furnace or air handler, and verify that it is off. Note that this may mean shutting off a circuit breaker that serves the furnace and air handler, and then, near the compressor, pulling out the disconnect block (or shutting off the 220-volt power) to the outdoor compressor.