Free cooling systems can have very high efficiencies, and are sometimes combined with seasonal thermal energy storage so that the cold of winter can be used for summer air conditioning. Common storage mediums are deep aquifers or a natural underground rock mass accessed via a cluster of small-diameter, heat-exchanger-equipped boreholes. Some systems with small storages are hybrids, using free cooling early in the cooling season, and later employing a heat pump to chill the circulation coming from the storage. The heat pump is added-in because the storage acts as a heat sink when the system is in cooling (as opposed to charging) mode, causing the temperature to gradually increase during the cooling season.
If the condenser coils are clogged, the compressor can overheat and shut down. You’ll experience intermittent periods of minimal cooling, followed by no cooling. Even if you’re “sure” the condenser coils are clean, clean them again. Turn off the power. Flip the air conditioning service and furnace circuit breakers in your main electrical panel to the “Off” position. Next, turn off the power switch right at the furnace or air handler. Then yank the disconnect block (Photo 1) and clean the condenser coils (Photo 2). If the air conditioning service still doesn’t work properly after you’ve cleaned the condenser coils, installed a new filter and opened all the supply vents, proceed with the following repairs.
My experience with Cody & Sons was an A+! I am always concerned with these companies taking advantage and charging more than they should. My technician, Mike, was on time, extremely professional and really knew his job. Prior to Cody & Sons, I had 5 other name brand HVAC companies service my furnace but no one could tell me why I smelled gas each time I turned my unit on. Several tried to sell me a new furnace. Mike thoroughly examined my unit and determined what the problem was. He then patiently explained it all to me in laymen's terms. I approved the work and Mike took care of it. I can't express the relief I feel knowing that my furnace is safe again and I am not inhaling fumes!!! From start to finish Mike took about an hour. The price I was charged was very fair! I am happy to say that I have finally found my go to HVAC company. THANK YOU, MIKE and Cody & Sons!!!
Terrible - Explained to tech that we had cold air on heat status. I placed Thermostat on emergency heat and was able to get some heat. I told him TXU had installed a a new thermostat and I think he may have installed it incorrectly but wasn't, sure. He said it would cost us more money if he fixed problem if there was one. He said I could pay for it and get reimbursed from insurance company. When he said it would cost us money I said I would live with it. I plan on calling a reputable repair company. He did not check furnace or temperature of house
Replacing a capacitor is easy. Just take a photo of the wires before disconnecting anything (you may need a reference later on). Then discharge the stored energy in the old capacitor (Photo 4). Use needle-nose pliers to pluck one wire at a time from the old capacitor and snap it onto the corresponding tab of the new capacitor. The female crimp connectors should snap tightly onto the capacitor tabs. Wiggle each connector to see if it’s tight. If it’s not, remove the connector and bend the rounded edges of it so it makes a tighter fit on the tab. When you’ve swapped all the wires, secure the new capacitor (Photo 5).