Air conditioner inverter Air door Air filter Air handler Air ionizer Air-mixing plenum Air purifier Air source heat pumps Automatic balancing valve Back boiler Barrier pipe Blast damper Boiler Centrifugal fan Ceramic heater Chiller Condensate pump Condenser Condensing boiler Convection heater Cooling tower Damper Dehumidifier Duct Economizer Electrostatic precipitator Evaporative cooler Evaporator Exhaust hood Expansion tank Fan coil unit Fan heater Fire damper Fireplace Fireplace insert Freeze stat Flue Freon Fume hood Furnace Furnace room Gas compressor Gas heater Gasoline heater Geothermal heat pump Grease duct Grille Ground-coupled heat exchanger Heat exchanger Heat pipe Heat pump Heating film Heating system High efficiency glandless circulating pump High-efficiency particulate air (HEPA) High pressure cut off switch Humidifier Infrared heater Inverter compressor Kerosene heater Louver Mechanical fan Mechanical room Oil heater Packaged terminal air conditioner Plenum space Pressurisation ductwork Process duct work Radiator Radiator reflector Recuperator Refrigerant Register Reversing valve Run-around coil Scroll compressor Solar chimney Solar-assisted heat pump Space heater Smoke exhaust ductwork Thermal expansion valve Thermal wheel Thermosiphon Thermostatic radiator valve Trickle vent Trombe wall Turning vanes Ultra-low particulate air (ULPA) Whole-house fan Windcatcher Wood-burning stove
Modern air conditioning systems are not designed to draw air into the room from the outside, they only recirculate the increasingly cool air on the inside. Because this inside air always has some amount of moisture suspended in it, the cooling portion of the process always causes ambient warm water vapor to condense on the cooling coils and to drip from them down onto a catch tray at the bottom of the unit from which it must then be routed outside, usually through a drain hole. As this moisture has no dissolved minerals in it, it will not cause mineral buildup on the coils. This will happen even if the ambient humidity level is low. If ice begins to form on the evaporative fins, it will reduce circulation efficiency and cause the development of more ice, etc. A clean and strong circulatory fan can help prevent this, as will raising the target cool temperature of the unit's thermostat to a point that the compressor is allowed to turn off occasionally. A failing thermistor may also cause this problem. Refrigerators without a defrost cycle may have this same issue. Dust can also cause the fins to begin blocking air flow with the same undesirable result: ice.
7) Schedule an annual tune-up with an HVAC professional. A trained HVAC technician can detect most problems before they become major ones. With a cost of around $100 for a routine maintenance call, the benefits will likely outweigh the costs by a considerable margin. A typical tune-up will include various tests to ensure your unit’s internal parts are functioning correctly, as well as a filter check, and a refrigerant charge if needed. Your technician will likely also clear the drain, and clean your unit thoroughly inside and out.