We are so happy with the service and the unit installed. Carlos, the sales representative, was very attentive to our needs at the time. He knew exactly what we needed for our a/c concerns. Brandon Hayword, the a/c installer was amazing. I have never seen a technician so meticulous. Every detail was attended to. Poor guy worked from morning till 4:00 Am the next day. Never heard a complaint or wanted to go home and call it a night. Again, thank-you for the great service.
Gainesville Mechanical Inc is open for regular business hours, Monday through Friday, from 8 a.m. to 5 p.m. We offer everyday extended business hours, at regular rates, to meet the challenge of your busy schedule with flexible appointment times, and always have a licensed technician at your door within 24 hours. For desperate times, we protect your home, comfort, and safety with 24/7 Emergency Assistance without added after-hour costs. Contact us at 770-532-9130, and rest assured, we prioritize your best interests. Our skilled service never comes with inflated or hidden charges. We provide affordable rates, upfront pricing, and the detailed information you need to make the best possible decisions. We service all makes and models of cooling equipment, optimizing safety, efficiency, and reliability, to deliver superior, ongoing performance. Trust our award-winning team of NATE-certified technicians to restore your comfort today, with repairs that ensure long-term satisfaction.
The concrete pads under home air conditioner and heat exchanger units tend to settle over the years. As long as there’s no strain on the copper coolant tubes and electrical lines, and the unit stays dry and level, it’s OK that the pad has sunk. But if it continues to sink and pulls the lines tight, or if water puddles around the unit, you’ll need to take action. Here’s how to fix it.
Reinstall the access panel and disconnect block. Turn on the circuit breaker and furnace switch. Then set the thermostat to a lower temperature and wait for the AC to start (see “Be Patient at Startup,” below). The compressor should run and the condenser fan should spin. If the compressor starts but the fan doesn’t, the fan motor is most likely shot. Shut off the power and remove the screws around the condenser cover. Lift the cover and remove the fan blade and motor (photo 7). Reinstall the blade and secure the cover. Then repower the unit and see if the fan starts. If it doesn’t, you’ve given it your best shot—it’s time to call a pro.
The burner can be fueled by gas or by oil. It is the component that creates the required heat. It can be controlled by a thermostat or by the fan limit control, which is located in the plenum chamber. A dirty air filter or a blocked fan can cause the burner to turn off and on more frequently than necessary. If you are experiencing this issue, the first thing you should try is to change the air filter. If that does not help the issue, contact UGI Heating, Cooling & Plumbing and we will send an expert technician to further troubleshoot your gas or oil furnace burner issues.
In a thermodynamically closed system, any power dissipated into the system that is being maintained at a set temperature (which is a standard mode of operation for modern air conditioners) requires that the rate of energy removal by the air conditioner increase. This increase has the effect that, for each unit of energy input into the system (say to power a light bulb in the closed system), the air conditioner removes that energy. To do so, the air conditioner must increase its power consumption by the inverse of its "efficiency" (coefficient of performance) times the amount of power dissipated into the system. As an example, assume that inside the closed system a 100 W heating element is activated, and the air conditioner has a coefficient of performance of 200%. The air conditioner's power consumption will increase by 50 W to compensate for this, thus making the 100 W heating element cost a total of 150 W of power.
Because an air conditioner moves heat between the indoor coil and the outdoor coil, both must be kept clean. This means that, in addition to replacing the air filter at the evaporator coil, it is also necessary to regularly clean the condenser coil. Failure to keep the condenser clean will eventually result in harm to the compressor, because the condenser coil is responsible for discharging both the indoor heat (as picked up by the evaporator) and the heat generated by the electric motor driving the compressor.