We were visiting our Arizona home from New York, when on one of the hottest days in August the air conditioning was not working. We called Precision & James Shelton worked to get the air up & running in no time. He was courteous & sympathetic, working hard to repair our central air…we have a warranty & Precision stands behind their work, they are available 24/7… Thank you!
All modern air conditioning systems, even small window package units, are equipped with internal air filters. These are generally of a lightweight gauzy material, and must be replaced or washed as conditions warrant. For example, a building in a high dust environment, or a home with furry pets, will need to have the filters changed more often than buildings without these dirt loads. Failure to replace these filters as needed will contribute to a lower heat exchange rate, resulting in wasted energy, shortened equipment life, and higher energy bills; low air flow can result in iced-over evaporator coils, which can completely stop air flow. Additionally, very dirty or plugged filters can cause overheating during a heating cycle, and can result in damage to the system or even fire.
The fan limit switch controls the furnace blower. The fan limit switch has three settings: “Fan On”, “Fan Off”, and “Limit”. In the “Fan Off” setting, the blower will only operate if there is warm air in the plenum to prevent cool air from blowing into the home. The “Fan On” setting will keep the blower operating even after the burner has shutdown, making sure that all of the hot air produced is circulated. The “Limit” setting is a safety control that will turn the burner off in the rare event that the air in the warm air plenum reaches an unsafe temperature. This may be the case if ducts are blocked or if the system controls are malfunctioning.
Close all the windows in the house, turn off all the fans and exhaust fans, and shut off the furnace. Light some incense and walk slowly around the outer walls of the house. Anywhere you notice the smoke blowing away from something or being sucked toward something, there’s probably an air leak. Now that you’ve found it, seal it! Here’s how. Here are more ways to improve energy efficiency in your home.
We contacted GatorAC and have been pleased through the entire process of the purchase, installation and the daily functioning of the unit. We spoke to Angie to get information about the Trane AC. She arranged for Carlos Garcia to come to the house to determine the unit that would fit our needs. We made the choice between 3 units on Thursday and the unit was installed Friday. The Installation team, Willie Shaw and Gary Barber were the best. When they left everything was done, clean and clear and working great. We would recommend GatorAC for your AC needs.
The Chartered Institution of Building Services Engineers is a body that covers the essential Service (systems architecture) that allow buildings to operate. It includes the electrotechnical, heating, ventilating, air conditioning, refrigeration and plumbing industries. To train as a building services engineer, the academic requirements are GCSEs (A-C) / Standard Grades (1-3) in Maths and Science, which are important in measurements, planning and theory. Employers will often want a degree in a branch of engineering, such as building environment engineering, electrical engineering or mechanical engineering. To become a full member of CIBSE, and so also to be registered by the Engineering Council UK as a chartered engineer, engineers must also attain an Honours Degree and a master's degree in a relevant engineering subject.
Dehumidification (air drying) in an air conditioning system is provided by the evaporator. Since the evaporator operates at a temperature below the dew point, moisture in the air condenses on the evaporator coil tubes. This moisture is collected at the bottom of the evaporator in a pan and removed by piping to a central drain or onto the ground outside.
If your AC doesn’t turn off when room temperature reaches the temperature set on the thermostat, the problem is generally occurring either at the thermostat or in the electrical system that runs the outside condensing unit. You can use the AC’s circuit breaker to shut off the unit, but that should not be a permanent solution—circuit breakers are not designed to be used like light switches.
When it comes to HVAC service in Cocoa Beach and throughout the Space Coast region, the team at Kabran Air Conditioning & Heating always has your best interests in mind. Not only do we provide the most innovative heating and air conditioning products from Carrier, we also offer flexible financing options, with approved credit, through Wells Fargo. Now you can enjoy your new furnace or AC system with additional financial benefits such as convenient monthly payments, competitive interest rates, and flexible payment options. To learn more about our financing options or to apply today, contact the premier HVAC company of Cocoa Beach today!
A lot of heat enters the home through windows, especially open windows. If you really want to control heat in your house, pay attention to your windows, too. Keep them closed and covered with blinds or drapes during the hottest parts of the day—especially windows that are currently facing the sun. Here are more tips for cutting cooling costs this season.
Air conditioner equipment power in the U.S. is often described in terms of "tons of refrigeration", with each approximately equal to the cooling power of one short ton (2000 pounds or 907 kilograms) of ice melting in a 24-hour period. The value is defined as 12,000 BTU per hour, or 3517 watts. Residential central air systems are usually from 1 to 5 tons (3.5 to 18 kW) in capacity.
If you hear clicking that is followed by a hum or buzz, you’re probably hearing the fan motor attempting to start without the boost it needs from the capacitor. You can almost always conclude that the capacitor has failed. Sometimes you can get the compressor fan spinning (clockwise) by pushing it with a thin stick or long screwdriver poked through the grille. But the chances are good that this might work for one cycle, but the capacitor will fail next time the AC goes on. It’s best to replace the capacitor.
The condensed, pressurized, and still usually somewhat hot liquid refrigerant is next routed through an expansion valve (often nothing more than a pinhole in the system's copper tubing) where it undergoes an abrupt reduction in pressure. That pressure reduction results in flash evaporation of a part of the liquid refrigerant, greatly lowering its temperature. The cold refrigerant is then routed through the evaporator. A fan blows the interior warm air (which is to be cooled) across the evaporator, causing the liquid part of the cold refrigerant mixture to evaporate as well, further lowering the temperature. The warm air is therefore cooled and is pumped by an exhaust fan/ blower into the room. To complete the refrigeration cycle, the refrigerant vapor is routed back into the compressor. In order for the process to have any efficiency, the cooling/evaporative portion of the system must be separated by some kind of physical barrier from the heating/condensing portion, and each portion must have its own fan to circulate its own "kind" of air (either the hot air or the cool air).